Commercial Plumbing Contractors Plumbing Service in Jacksonville, FL (32209)
Date: April 14, 2023
ZIP Code: 32209
Plumber Notes: There was water in the women's bathroom, in the ADA stall. Do upon my inspection I found water in the floor back wall behind the toilet. I got permission to cut up the wall, when I cut up the wall there was a decent amount of water along the framing tracks. This issue has it has been ongoing for at least 3 to 6 months. I shop vac the dirty water. Once it was all clean, I found out the leak was coming from the opposite wall and the leak was coming from in the kitchen where the mop sink was that so I remove the mop sink and I found out that the gasket underneath the mouth sink was worn down, and and I found out that the 3 inch pipe drainage was cracked, so I chipped out the surrounding area where the 3 inch pipe was, I I cut out the crack area. I install a 3 inch Fernco. I install a new 24 x 24 x 10“ mop sink. I recaulk I mop sink area after the installation. I pour about 5 gallons of water into the mop sink, just to check to see if there was any more leaks, and there was no more leaks. For the bathroom I remove the toilet and I remove the laboratory in the ADA stall. And we will be coming back to reinstall the toilet and the lavatory. Once the tile work is done. I install a new angle stop for the toilet due to the previous angle stop was leaking. and in the bathroom, there is four floor fans blowing towards the wall, so that we can dry it wet area in the wall. We will be picking up the fans on Monday.