Commercial Plumbing Contractors Plumbing Service in Jacksonville, FL (32207)
Date: December 15, 2020
ZIP Code: 32207
Plumber Notes: 2 man gas leak detection in the Gymnasium. Capped off all of the gas heaters in the gym and pumped up the gas to 20 pounds of pressure. On Monday the 7th of Dec we found a leak on the main shut off for the gas water heater in the boys locker room. After fixing the leak and replacing the shut off at the water heater, came out and found another leak, we returned on Wednesday and continued testing all of the gas pipe in the ceiling of the gym and all over the gym. We found a leak on a 6 inch long 2 inch nipple coming off the Main gas line from the meter. Returned Thursday the 10th of Dec and repaired the leak on the 2 inch nipple. Called to come out and check there meter and connections, when the technician came out he told customer that there were no more leaks and the gas company turned on the gas again. Returned Friday to reconnect all of the heaters in the gym.