Slab Leak Repair Plumbing Service in Jacksonville, FL (32217)
Date: October 16, 2023
ZIP Code: 32217
Plumber Notes: Customer had slab leak. Provided repipe estimate to her and we will return Monday to start the repiped. Returned Monday 10/2 to complete repipe. Replaced copper water service from Shutoff valve in front yard to all fixtures in house. Replaced main shutoff with Brass 1/4 turn Ball valve. Ran all new CPVC water lines in attic to all fixtures. All water lines are strapped and insulated within Code in the attic. CPVC is dropped down wall and pipes to all fixtures, and secured when passing through studs. Stud guards are also installed where applicable. Hose bib in front yard, as well as back yard is live, and they have Vacuum Breakers installed per Code regulations. Job was completed within three days. Hammer arrestors installed on all fixtures with Solenoids. No leaks, drips, or line breaks upon departure. Price to repipe entire house from Main shutoff to all fixtures. Scope of work includes routing all new water pipe throughout the attic and down the walls to all fixtures. We will replace shutoff valve at front of house as well as hose spigot. We will also insulate all piping in attic and all exposed water lines. We will have to cut an access in the attic to reach the sealed off portion, containing the kitchen andaster bathroom. Job is scheduled for four working days, and four technicians. We will provide all materials.