Residential Plumbing Services Plumbing Service in Jacksonville, FL (32219)
Date: October 16, 2023
ZIP Code: 32219
Plumber Notes: Replaced failed pressure switch on exposed pump for Aerator system between the garage and dispatch building. After replacement of pressure switch, pump turned back on and was able to maintain a constant pressure. Tested to make sure new switch activated and deactivated pump at appropriate intervals. No leaks or pressure loss upon departure. Would recommend replacement of Aerator system with new Softener and UV filter, as it is a more cost effective system and provides a better quality of water for consumption. Estimate for new system and installation is available upon request.