Residential Plumbing Services Plumbing Service in Jacksonville, FL (32225)
Date: September 22, 2023
ZIP Code: 32225
Plumber Notes: Upon arrival noticed the aerator was empty and fitting had blown out of connection at top of pump. Repaired. The water pipe going from pump to the aerator went to turn the power on notice. The pump that fills the aerator was not responding so then I inspected the pressure switch and notice at the points were burned out on it. So I then replaced the pressure switch and returned the power and it started filling up the aerator. After the aerator was completely full, I then turned on the second pump which controls pumping the water from the aerator to the house and the house has water again with good pressure.