Residential and Commercial Plumbing Services in Palm Coast
Our family of plumbers have served Northeast Florida for two generations.
Betros Plumbing is a full-service commercial and residential plumbing company serving Palm Coast and the greater Northeast Florida area. We provide plumbing services near you. Below are just a few ways our plumbers have helped local businesses and families recently.
Recent Palm Coast Logs
Slab Leak Repair Plumbing Service on June 8, 2021 in Palm Coast, FL (32137)
Plumber Notes: Attempted to remove a 10 in. wheel valve inside the pump room beside pond. Five additional pumps were needed to aid the removal of water. Due to how the water intake is for the pond circulating pump we were not able to stop the water flow and needed to remove most of the water from the pond before beginning work. Unable to leave the pond pump unsupervised due to the residence at the property we were there for 30 hours removing water. Once the water was removed we attempted to replace the 10 Butterfly valve and were unsuccessful due to new design of valve and existing impressions the valve made against the rubber spanflex coupling. Rebuilt existing 10 in. Butterfly valve and reattached the handle and made it sturdy. Attempting to reinstall rebuilt butterfly valve the brittle 10 in. flange cracked. Needed to cut back on flange and replace the flange then replace all of existing pipe from pump to spanflex coupling. After install of new pipe and test, all is holding well and not leaking. Also added a brace to bottom of pipe making the pipe much more stable.... read more
Complete Re-Pipe Plumbing Service on April 16, 2021 in Palm Coast, FL (32137)
Plumber Notes: Replaced 8-10 inch flanged pipe section of pipe coming from pump per proposal. ... read more
Commercial Plumbing Contractors Plumbing Service on July 16, 2021 in Palm Coast, FL (32137)
Plumber Notes: Customer needed butterfly valve closed and to verify 100% it was closed. I spun wheel until the dial was directly pointed to closed...then I opened flange behind valve and made sure the water lost pressure and died down. Water pressure died down and shut off completely.... read more
Commercial Plumbing Contractors Plumbing Service on June 15, 2021 in Palm Coast, FL (32137)
Plumber Notes: Tub drain was leaking, there was no washer, old putty was blocking threads, needed new tub and overflow drain. Replaced with new waster drain and overflow. Had to bust out concrete from unit below. ... read more